Jasper GA Plumbing Services
Jasper GA Plumbing Repair & Replacement
Looking for a Jasper, GA plumber you can trust? Look no further than My Georgia Plumber. We've been in business for over 30 years, and we're experts in all things plumbing. From drain cleaning and repair to sewer and water line services, we've got you covered. We also offer gas line services, bathroom and kitchen plumbing and laundry room plumbing. Plus, we're happy to help with any remodeling projects you might have. Give us a call today - we're always here to help!
for Jasper, GA
George - Jasper, GA 30143
Robert was great, informative & awesome personality!!
Southeast - Jasper, GA 30143
Thank you for your kindness and service!
CUSTOMER STATED: The homeowner complaint is that when they try to use the walk in bath tub they run out of hot water after 1/3 of the tub is filled TECHNICIAN NOTES: I tested the water and it never got over a warm temperature In any of the fixtures that are connected to the original water heater I then looked at the water heater and found that it is 28 years old and the homeowner could not tell me if it had ever had any maintenance performed I found the temperature on the water heater was set low at somewhere around 110 to 115 I turned the temperature up and found that the water temperature did rise I then started filling the walk in tub up and got about half way up before the water started cooling down that was with only turning up the temperature on the upper thermostat RESOLUTION/RECOMMENDATIONS: My recommendation is to replace the water heater JOB NOTES: JOB STATUS: COMPLETE/NOTCOMPLETE (RETURN TRIP NEEDED?) Job not completed waiting for choice home warranty
The homeowner complaint is that the kitchen sink is not draining I found that kitchen drain line was clogged and backing up in the the sink bowls I ran my Sink machine and cleared the clog Tested with no issues Job completed Autho Estimates are built and ready ready to send
CUSTOMER STATED: toilet leaking water to bowl TECHNICIAN NOTES: came out today for diagnosis found toilet was faulty due to a flapper replacement of flapper is recommended to fix concern today RESOLUTION/RECOMMENDATIONS: replaced flapper found no further issues JOB NOTES: JOB STATUS: COMPLETE PARTS: (IF INCOMPLETE ARE STOCK OR SPECIAL ORDER PARTS NEEDED?) AUTHO: submitted to choice ESTIMATES: (READY TO SEND OR NEED REVIEW)
I handled this one after I got back yesterday but it was on my schedule twice.
AHS is shipping a new 40 gallon propane power vent water heater to our shop for replacement. We will be supplying the 50 gallon electric water heater.
Customer States: Both water heaters in basement are leaking. Water was turned off to both units and drained to prevent further damage. Technician Notes: Out today to look into issue with two water heaters leaking in the basement utility room. Unit on the left is a 40 gallon propane power vent water heater from 2000. Unit on the left is a 50 gallon electric from 2007. Both units have failed. Both units will need replaced with code requirements and a permit.
CUSTOMER STATED: sewer smell from upstairs bathroom, could be wax ring TECHNICIAN NOTES: came out to location for diagnosis today for upstairs guest bathroom having sewer smell issues, as I walked in I found home owner had some sewer flies around shower areas, to test issue out I ran water in the sink and I could hear water running through shower area ptrap in walk in shower is dry. RESOLUTION: ran water in shower for around 20 seconds and retested with no further issues, tested toilet multiple times for leaks but found none did explain to home owner of running fixtures at least once a month to make sure sewer smells don’t come back up. MGPNOTES: JOBSTATUS: complete. ESTIMATES: AUTHO:
CUSTOMER STATED: whirlpool tub was leaking and not working TECHNICIAN NOTES: after inspecting, I found the leak is coming from one of the jet wines towards the faucet side of the jetted tub. The lower jets would not work due to an electrical error on the switch. RESOLUTION: explain to the homeowner is that my daughter plumber does not need repair the Jets and or the electrical switches on these Jacuzzi tubs and that we will submit to choice to transfer the vendor to a Jacuzzi tub specialist JOB NOTES: job status is complete STATUS not a plumbing related issue AUTHO I will need to submit in the morning I do not have signal where I am at for quite a while ESTIMATES no estimates at this time
CUSTOMER STATED: Shower consistently dripping TECHNICIAN NOTES: Tub/shower unit in basement was dripping. Homeowner had attempted to remove and replace cartridge but became stuck with bonnet nut. RESOLUTION: Customer requested to use part he had purchased, built estimate and advised that with a customer supplied cartridge there was NO part’s warranty from My Georgia Plumber. Agreed and signed off on estimate. During repair I found the entire valve (on CPVC) was installed crooked and caused alignment issues. One trim plate screw is stripped and due to being on CPVC I left approximately a 1/2 inch out so as not to apply too much pressure. Additionally the screw that attaches the handle to the cartridge is missing so the handle can come off during use. Homeowner advised of both concerns. JOB NOTES: STATUS Complete AUTHO Please bill card in pictures. ESTIMATES Remove existing delta shower cartridge and install customer supplied cartridge. Please note if us
Customer stated: toilet in powder bathroom is still running Technician notes: upon inspection found fill valve tube stuck down inside of overflow tube, was unable to find any other mechanical failures with the toilet, replaced fill valve tube and installed overflow clip. MGP notes: this is a legitimate call back. Estimates: no further needed Job status: complete Autho: added additional not online for choice