Nelson GA Plumbing Services
Nelson GA Plumbing Repair & Replacement
My Georgia Plumber is a trusted plumbing service company that has been serving the Covington, GA area for over 30 years. We offer a wide range of residential and commercial plumbing services, including drain cleaning and repair, sewer line and water line services, water heater services, gas lines, bathroom, kitchen and laundry plumbing and remodeling services. We are dedicated to providing our Covington customers with the highest quality of service possible, and we believe that our experience and reputation speak for themselves. If you are in need of a plumber, please give us a call today!
for Covington, GA
CUSTOMER STATED: Customer very recently moved into the building. Behind their washing machine on their bottom floor had been leaking and so much so that a bubble built them burst on to the floor. The basement toilet needed to be re adjusted to have the water at the appropriate level so it won’t keep running. The kitchen sink both sides were leaking out from the strainer into the cabinets. TECHNICIAN NOTES: The issues were able to be easily found and addressed. RESOLUTION/RECOMMENDATIONS: We needed to replace the washer in the connection to the washing machine hose. For the basement toilet that was still running we had to adjust the fill valve to stop the overflowing water in the tank. We need to detach the basket strainer and install some plumbers putty in both sides to complete the seal. JOB NOTES: Washing machine task is complete. Basement toilet is no longer running. Both sinks no long are leaking. JOB STATUS: COMPLETE PARTS: Washer, Plumber putty. AUT
CUSTOMER STATED: Their kitchen sink was leaking water into the cabinet underneath. TECHNICIAN NOTES: The basket strainer on the right side of the sink was extremely lose, see video. RESOLUTION/RECOMMENDATIONS: Tighten up the basket strainer for the right side of the sink and put new plumber putty. JOB NOTES: We took apart the basket strainer and the draining pipes. We rebuilt it with plumbers putty and properly reattached the connections. We tested the system, no leaks found. JOB STATUS: COMPLETE AUTHO: Resipro.
CUSTOMER STATED: TECHNICIAN NOTES: RESOLUTION: JOB NOTES: STATUS AUTHO ESTIMATES
Customer stated: kitchen sink faucet is leaking. Technician notes: upon inspection found that kitchen sink pull out sprayer was very loose, tightened sprayer and no more leaks were found. During inspection found that dishwasher drain hose was not secured to kitchen drain, secured drain hose using a hose clamp.
Arrive at this house not one answer the door
Out today to address tenant concern of leak in the basement. Upon investigation I found that the leak is coming from the jack and Jill hallway bathroom shower drain. The shower drain is currently deteriorating and causing the leak. This drain is on 2 inch ABS pipe. The drain in the shower will need to be replaced along with the pipe/trap to allow to connect back properly. Job complete Please submit for Autho Estimate created
CUSTOMER STATED: Kitchen sink leak/ back up TECHNICIAN NOTES: When I arrived the dishwasher was running and draining Upon further inspection I found that the extension tub on the basket strainer on the left side was detached. RESOLUTION: I determined there was no clog. I added a longer extension tube and a new Ferrell. Tested both sides and restarted dishwasher JOB NOTES: STATUS Complete AUTHO Bill out ESTIMATES None needed
CUSTOMER STATED: High water bill. TECHNICIAN NOTES: upon arrival checked meter and it was continuously spinning (see video) upon out inspection found water puddling on right side of front by tree line, will need to dig up area to determine what is leaking, pipe is more than 18 inches underground from what I can tell at this time. RESOLUTION: main water line will have to be dug up and repaired or replaced. JOB NOTES: will have to schedule another day to dig up and make repairs. STATUS: job is not complete at this time. AUTHO: ESTIMATES: no further needed
Customer stated: master bathroom toilet is leaking. Technician notes: upon inspection found master bathroom toilet leaking from tank to bowl gasket, emptied and removed tank, cleaned gasket and toilet, reinstalled tank with new metal washers and nuts, no active leaks are found at this time. MGP notes: Mr. Chris will create invoice and bill. Job status: complete Estimates: no further needed
CUSTOMER STATED: downstairs shower was not turning all the way off TECHNICIAN NOTES: upon inspection found a single handle delta monitor shower valve that would not turn off all of the way. RESOLUTION: removed existing cartridge and installed new My Georgia Plumber supplied delta shower cartridge. JOB NOTES: Mr. will create invoice and bill resipro STATUS: complete ESTIMATES: no further needed