Mableton GA Plumbing Services
Mableton GA Plumbing Repair & Replacement
Looking for a plumber you can trust? Look no further than My Georgia Plumber. We've been providing residential and commercial plumbing services in Mableton, GA for over 30 years. Our services include drain cleaning and repair, sewer line and water line services, water heater services, gas lines, bathroom, kitchen and laundry plumbing and remodeling services. We're dedicated to providing our Mableton customers with the highest quality plumbing services possible. Contact us today to schedule a consultation. We're looking forward to meeting you!
for Mableton, GA
David - Mableton, GA 30126
Response from My Georgia Plumber:
Thanks for leaving us such a wonderful review. We are glad that you loved our services, our dedicated staff will be pleased to learn of your high praise.
My Georgia Plumber
Linda - Mableton, GA 30126
Linda - Mableton, GA 30126
Excellent service and very professional. Would highly recommend
Annual Whole Home Plumbing Inspection Upon inspection I found that the thermal expansion tank located in the garage of home has failed, and is full of water which means it is in need of replacement. I presented options to have the tank replaced, and home owner elected to wait, but stated he definitely wanted to get it taken care of soon. Overall everything in home has been upgraded, and maintained. Everything is in great condition, and functioning properly. Job Status: Completed Estimates: Please FWD
The homeowner complaint is they are having a water leak there water bill has jumped up twice I found that they are having a water leak and it is on the main water line I tested the system by turning off the main water shut off in the basement and you could hear water running sound coming through the pipe The meter is spinning at a good rate so it seems to be a fairly large leak But there is no signs of a leak in the yard The water line does go under the driveway and under the sidewalk to the front door of the home The water line coming off the water looks to be 1in Job completed Estimates are built and ready to send
The homeowner complaint is that the master bathroom toilet is still running I found that the master bathroom toilet is still running It is due to the flapper being old and worn out This is not a warranty I replaced the flapper in the master bathroom toilet Tested with no issues Authorization115agra Job completed No new estimates are needed
Cut off and replace 2 delta shower handles manufacturer supplied parts 1 master bath shower 2 guest bath tub/shower Technician notes: cut off handles in hall bathtub and master shower, installed new delta cartridges then replaced handles with new customer supplied delta handles. Estimates: no further needed Job status: complete
This is a complimentary estimate to hydro jet the main sewer line for the home. We would access the drain line from the 6" city clean out located in the front yard and work back toward the home to allow any blockage to flow toward the larger city drain. Once the hydro jetting is complete, My Georgia Plumber recommends that a camera be run to ensure that the blockage has been removed and that there are no additional underlying issues. PLEASE NOTE: If the customer declines the camera inspection, My Georgia Plumber will be unable to warranty the hydro jet work. Came out today to further inspect sewer line issue. Brought camera and hydro jet. Pulled cleanout in crawlspace to find clog inside of the san tee. This fitting is improper. Should have been a combo to allow for better turn. This section also has slight back fall. Cleared stoppage out of tee. Ran hydro jet into sewer line. Was unsuccessful using hydro jet to blow through line. Ran camera into drain. There is a belly going und
The complaint is that the tenant heard a loud Burst sound followed by water flowing I found there is a small section of cpvc that has cracked between 2 fittings In order to fix it there are several tees and about 3 feet of pipe that will need to be cut out and replaced Cut out the section of cpvc that has cracked along with several tees and reconnect everything with pex Job completed No new estimates are needed
CUSTOMER STATED: there’s a pin hole leak in the basement bathroom of home TECHNICIAN NOTES: came out today to replace that damaged piping, no repair possible due to it leaking. RESOLUTION: Replaced the damaged piping with PEX and found no further issue of a leak, I will notate that the area may have a rodent issue so work will not have warranty. I spoke to home owner about addressing rodent issue to prevent further damage to her water lines in her home. MGPNOTES: JOBSTATUS: complete ESTIMATES: None AUTHO: This is a complimentary estimate to repair a 1/2 inch polybutylene line located in the ceiling of the basement bathroom. PLEASE NOTE : My Georgia Plumber does not repair/replace drywall removed.
CUSTOMER STATED: toilet in master bathroom keeps running, the toilet in hallway will occasionally run TECHNICIAN NOTES: came out today to diagnose issues, I found that hallway bathroom had no issues of turning on and off so I didn’t further diagnose. The master bathroom toilet was having issues with turning on at random moments so I addressed the fill valve. RESOLUTION: Replaced the fill valve and found no further issues on toilet today it is working correctly. I did replaced the pressure regulating valve due to the fact that pressure was over 80 once I replaced the pressure regulating valve I found no further issues with pressure. MGPNOTES: JOBSTATUS: Complete ESTIMATES: Send complimentary estimates AUTHO : PRV pressure is high and is showing signs of damage inside the home the toilets are running non stop, and a faucet is starting to drip replacement is recommended to address issue
Andrew Customer stated- Water heater not working, gas line twisted Technician notes- Found a heater from 2006, t&p is leaking, vent not connected properly, expansion is on the other side of the basement, found 2 pin holes, found supply line for dishwasher leaking, found tubular in kitchen cracked.
This estimate is to replace the hall bathroom glacier bay single handle shower cartridge. Advised customer that we would have to try and locate the cartridge, if unable to do so we would have to order it or replace the complete shower valve. Technician notes: glacier bay shower cartridge will need to be replaced, we will have to order part and return to install it. MGP notes: customer advised that the house will be vacant so it is available whenever part comes in Job status: will have to order part and return to install it. Estimates: please forward to customer. Autho: received Autho via recorded phone call.