Peachtree Corners GA Plumbing Services
Peachtree Corners GA Plumbing Repair & Replacement
If you're in need of a plumber in Peachtree Corners, GA, look no further than the experienced professionals at My Georgia Plumber. We've been in business for over 30 years, and our residential and commercial plumbers are some of the best in the business. We offer a wide range of services, including drain and sewer services, water heater services, gas line installation and repair, bathroom, kitchen and laundry plumbing services and remodeling services. No matter what your plumbing needs are, we're here to help. Give us a call today to schedule a consultation. We're looking forward to serving you.
for Peachtree Corners, GA
CHW SENT OVER NEW WORK ORDER - TRADE FEE REQUIRED IS $75.00. MUST COLLECT THIS FOR THE APPROVED WORK ORDER SENT. Replace the sewage ejector pump and float switch And check valve Return trip to replace the existing sewage ejector pump and check valve in the basement bedroom closet behind a trap door. Tight quarters for replacing the pump. Managed to remove old unit and install a new sewage ejector pump that has a new switch, rebuilt discharge line with a new check valve. Tested for proper function and leaks. Job Status: Complete.
CUSTOMER STATED: the homeowner complaint is that the sewage ejector pump is not working TECHNICIAN NOTES: I found signs that the sewage ejector pump did not pump And flooded the basement After testing the system I found that the pump is working but the float switch is not working RESOLUTION/RECOMMENDATIONS: My recommendation is to replace the sewage ejector pump and float switch JOB NOTES: JOB STATUS: COMPLETE/NOTCOMPLETE (RETURN TRIP NEEDED?) Job not completed PARTS: (IF INCOMPLETE ARE STOCK OR SPECIAL ORDER PARTS NEEDED?) Sewage ejector pump and 2in check valve AUTHO: (AUTHO CODE OR WHO YOU SPOKE TO) Submitted online ESTIMATES: (READY TO SEND OR NEED REVIEW) Are built and ready to send
This estimate is for my Georgia plumber to supply and install toilet, we will remove old toilet and haul off, once installed we will test all connections Technician notes: disconnected and removed the existing crane toilet that is cracked, installed new comfort height elongated toilet, no leaks or mechanical failures are happening at this time. MGP notes: please bill accordingly Job status: complete Estimates: no further needed
CUSTOMER STATED: Toilet leaking from tank TECHNICIAN NOTES: arrived to find toilet on 2 floor leaking from the tank, upon further diagnosis we discovered to tank was cracked and will need a new toilet. RESOLUTION: Submitted to choice home warranty for replacement. JOB NOTES: STATUS- waiting on autho AUTHO- submitted ESTIMATES- do not send until we get autho
CUSTOMER STATED: I want an estimate to add a second hose bib to the rear of the house and extend the current hose bib approximately 15 feet TECHNICIAN NOTES: I discussed with the homeowner on what he wanted to do and determine the best solution was to run an exterior line underneath the rear porch and half-inch pecks, approximately 25 feet in total length. He does not want us to drill through the bottom of the porch instead would like us to run it up the side and is aware that text is not warranted if exposed to UV rays and would like us to cover up the expose section with the foam. He homeowner is also aware that due to it being an exterior water line, he will need to winterize a each year Corvette images in the line freezing RESOLUTION: presented him the estimate to install two new hose, bibs and replace the emergency shut off as well as add a drain down to prevent a line from freezing and to properly winterize this exterior line. After presenting the estimate, he would like the e
CUSTOMER STATED : Would like an estimate to jet a floor drain line. TECHNICIAN NOTES : Out today for the concern of the business owner interested in having a floor drain jetted out. While inspecting concerns, the business owner stated not all floor up. Only one backs up initially and when it gets really backed up, sewage will begin to come from floor drain where the water heater is located. I have recommended to camera the floor drain line to ensure of what is causing the issues and then go from there about offering solutions for his concerns. The customer has stated he will call back in the office this afternoon to sign the complimentary estimate to camera the floor drain. RESOLUTION : No work done today. ESTIMATE ONLY. JOB NOTES : No payment to process at this point in time Job complete Please forward the complimentary estimate to email in pinned notes PLEASE REACH OUT TO BUSINESS OWNER FOR SCHEDULING.
Customer stated upstairs guest bathroom, shower with whistle periodically and sporadically when turned on Technician notes after inspecting I found that the pressure did not seem high off the Fossetts, but the shower with fluctuate a whistling noise once another faucet was turned on. Resolution I remove the flow restrictor to solve this issue as the homeowner stated he installed a new showerhead recently to correct this issue. After turning on the shower for approximately 10 minutes the whistling noise never reappeared. MGP notes homeowner was interested in our membership as well as a tankless water heater flush Job status complete Estimate notes please send estimate
CUSTOMER STATED: TECHNICIAN NOTES: RESOLUTION: MGP NOTES: No one on site waited 30 minutes and left a door hanger. ESTIMATE NOTES: AUTHO: JOB STATUS: need to reschedule