Nelson GA Plumbing Services
Nelson GA Plumbing Repair & Replacement
My Georgia Plumber is a trusted plumbing service company that has been serving the Forest Park, GA area for over 30 years. We offer a wide range of residential and commercial plumbing services, including drain cleaning and repair, sewer line and water line services, water heater services, gas lines, bathroom, kitchen and laundry plumbing and remodeling services. We are dedicated to providing our Forest Park customers with the highest quality of service possible, and we believe that our experience and reputation speak for themselves. If you are in need of a plumber, please give us a call today!
for Forest Park, GA
Customer Stated: The water heater wasn’t working. Tech Notes: Upon inspection I found that this is a rheem 40 gallon natural gas water heater located in the garage of home, and is only 2 years of age which is still under manufacture warranty. I found that the gas meter has been locked which means this tank is not getting any gas to it, and is the cause for the hot heater not being able to function properly. I let the tenant know that he needs to contact ResiPro or the gas company so they can come out, and unlock his gas meter. I can not legally unlock this meter. Resolution: The tenant needs to contact ResiPro or gas company to have his gas meter unlocked. Job Notes:**ResiPro needs to have the gas meter unlocked**This house is on septic, and there are no external C/O**PLEASE BILL OUT TO RESIPRO FOR TODAYS DIAGNOSIS TRIP** Job Status: Complete Estimates: N/A
CUSTOMER STATED : Sink is leaking. TECHNICIAN NOTES : Out to the residence today for the tenants concern of the kitchen sink leaking. When I arrived, I found that both left and right sink basket strainers were loose and leaking when water is being ran. RESOLUTION : Replaced both left and right basket strainers for the kitchen sink. After repairs were made, I have filled both sides of kitchen sink up half way and let water drain to test for leaks. At this point in time, water is draining properly and there are no leaks, drips, or concerns appearing under the kitchen sink. JOB NOTES : No exterior clean out located on the property. please bill resipro for invoice amount. JOB STATUS : Job complete
Customer stated: out today on sold estimate to replace washing machine box. Tech notes: removed old box cut out cpvc and went back with pex and used fernco to hook drain back up. Resolution: turned water on to home and tested washing machine box. Everything is working fine at this time no leaks. Mgp notes: none needed Estimate notes:sold Job status: complete CLN NOTES - BILLED IN PORTAL.
Customers washing machine has hot and cold lines were busted due to freezing. Will need to completely replace the washing machine box and up to 10ft of half inch pex to resolve the issue. CLN NOTES - SUBMITTED TO RESIPRO FOR APPROVAL.