Nelson GA Plumbing Services
Nelson GA Plumbing Repair & Replacement
My Georgia Plumber is a trusted plumbing service company that has been serving the Temple, GA area for over 30 years. We offer a wide range of residential and commercial plumbing services, including drain cleaning and repair, sewer line and water line services, water heater services, gas lines, bathroom, kitchen and laundry plumbing and remodeling services. We are dedicated to providing our Temple customers with the highest quality of service possible, and we believe that our experience and reputation speak for themselves. If you are in need of a plumber, please give us a call today!
for Temple, GA
This is an estimate to replace the main water line from the meter to the foundation connection (outside the home). This will be replaced in 3/4 inch pex. Once new WO is received in the portal we will call to schedule with the homeowner/tenant. Install 100ft of new water line tested and everything is good job is complete
We were called out today to investigate a possible leak, as the water meter is constantly running according to the customer. After arriving at the location, we found that the leak is in the front yard but there are no visible signs of it. To accurately locate the leak, we recommend using leak detection services. Once the leak is pinpointed, we will proceed with the necessary repair. Unfortunately, we couldn't find a clean-out during our inspection. The job is complete, and we will provide an estimate for leak detection to locate the leak in the yard.
Replaced existing copper ice maker water line from under the kitchen sink to the refrigerator. New stainless steel braided supply line is connected and water is on with no leaks or issues at this time. Will put together an estimate on cutting out the existing saddle valve and reconfiguring a new isolation valve for the ice maker supply line.
CUSTOMER STATED: TECHNICIAN NOTES: RESOLUTION/RECOMMENDATIONS: JOB NOTES: JOB STATUS: COMPLETE/NOTCOMPLETE (RETURN TRIP NEEDED?) PARTS: (IF INCOMPLETE ARE STOCK OR SPECIAL ORDER PARTS NEEDED?) AUTHO: (AUTHO CODE OR WHO YOU SPOKE TO) ESTIMATES: (READY TO SEND OR NEED REVIEW)
Customer called about a clog. I found a clog between the house and clean out outside. We cleared the clog this time, but I recommend to come back with the large camera to give proper diagnosis because I felt something in the line with the small machine and this problem can happen again.
CUSTOMER STATED: Small puddle of water on the floor and the ceiling is slightly stained. TECHNICIAN NOTES: Out to the residence today for the concern of water on the floor and the ceiling being slightly stained. When I arrived to the residence I rang the door bell several times and also knocked on the door several times. Although there is a car in the driveway and a light on outside, no body answered the door. I’ve waited 10 minutes and have had no luck. We will need to get in contact with the tenant and schedule a better time when they’ll be available. RESOLUTION: Did not go inside home today. JOB NOTES: Job not complete Need to reschedule Please bill resipro for trip out. STATUS AUTHO ESTIMATES
Customer stated kitchen faucet sprayer came loose Technician notes after inspecting a found at the sprayer was not installed correctly and just needed to be re-thread it onto the spring line Resolution after installing the integrated sprayer on the chrome kitchen faucet, I tested and found no further issues with this faucet, and it was properly install Job status complete Authorization submit to resipro for today’s invoice No estimate at this time
CUSTOMER STATED: kitchen sink is leaking from left side TECHNICIAN NOTES: came out to location for diagnosis found kitchen sink on left side was leaking, while diagnosing I found the tubular was loose. RESOLUTION: tightened the tubular and found no further issues while draining sink multiple times. The tubular gaskets where not sat right causing water to push through. JOB NOTES: STATUS: complete AUTHO ESTIMATES
CUSTOMER STATED : Need a new toilet supply line, new whole home shut off valve, and need to rework out kitchen sink drain. TECHNICIAN NOTES : Out to the residence today for a sold estimate to replace the existing whole home shut off valve, the existing toilet supply line for the toilet in the master bathroom, and also to rework all drainage located under the kitchen sink on the main level. Before beginning any work, I tested the water pressure and found the existing pressure regulating valve has failed causing the water pressure to be 130 PSI. Service estimate to also replace the pressure regulating valve has been signed off during todays visit. RESOLUTION : Replaced the existing toilet water supply line for the toilet in the master bathroom on the main level, replaced the existing whole home shut off valve in the garage as well as the pressure regulating valve also located in the garage, and all drainage plumbing under the kitchen sink has been reworked and piped the correct
Customer stated: garbage disposal pipe is loose, master bathroom toilet supply line needs replaced and whole home shut off needs replaced Technician notes: upon inspection found kitchen sink drain needing to be completely re ran, cpvc whole home shut needs to be replaced with new brass shut off and master bathroom supply line needs to be replaced. MGP notes: customer would like to pay full amount for estimate today, please bill card in photos Estimate: please forward Job status: will return to complete sold estimate